Operation Management and Maintenance
1, using of the storage tank must follow the rules of the “ Pressure Vessels and Technical Supervision Regulation” and other relevant laws and regulations strictly for safety technology management and prohibit overloading, over temperature and overpressure to ensure the security usage of the tank.
2, technical director of the users is responsible for the pressure vessels safety and technical management, the specify the professional technical personnel for the daily technical management of the pressure vessels.
3, The tank operationers should be tested and approved by the safe education training and get the related certificates.
4, cooling measures must be taken when any of the following circumstance occurs.
A, the pressure gauge indicating the value gets close to the red line, or the pressure is keep increasing.
B, the temperature gauge indicate the value reaches the yellow warning signs.
5, when the tank pressure meet the designed pressure value(the red line indicating value) and the safety valve does not open, the operator should take immediate measures to reduce the pressure of the tank first, the close the cut-off valve under the safety valve for maintenance, calibration, and rapidd installation of the safety valve to let the tank back to the normal working condition.
6, the storage tank should be tested regularly in accordance with the related rules in “ Pressure Vessel Safety Technology and Supervision Code” .
Supplement: comparison table for Liquid level, volume and Weight
The inner diameter of the tank is 2800mm, shell length 7180mm, head cover straight flange 40mm
More information, please feel free to contact with Ms. Anita Deng.
Whatsapp: +86 13329899995